Covid-19: We are manufacturing, working and supplying as normal in-line with government guidelines
In this article, we’ll be looking at alternative utility pole options and giving an overview of their effects on safety, maintenance and overall environmental impact. We will also take a look at alternative readily available solutions used to extend the life of standard treated wooden power and telecom poles.
The following information is from a report published by AquAeTer, Inc regarding an environmental lifecycle assessment of wooden, steel, concrete and composite poles (Full report available on request). The products used in the report represent general product categories, which are subject to different designs and material contents. Three of the most commonly used alternatives to wooden poles are steel, steel-reinforced concrete and composite/plastic. The composite poles use a fibreglass construction, sometimes featuring an outer plastic coating. From an initial cost standpoint, all of the above options, as a general rule, incur a more significant initial purchase cost, with composite being particularly expensive due to its resource requirement for production.
While we might assume that these more costly alternatives provide longer life, they are subject to many of the same issues of failure as wooden poles. Although traditional leaching and decay that we see in wooden poles are not present, both concrete and steel poles suffer from ground line corrosion this effect being made worse where poles are installed in acidic soil conditions. The lifespan of composite poles used in ground contact is currently an unknown with osmosis being a potential issue where conventional polyester resin systems are used. Osmosis significantly weakens composites over time. More costly epoxy resin systems offer much greater resistance to osmosis as do plastic encapsulated composites.
Anecdotal evidence indicates that concrete and steel poles typically have a service life of around 40 years. Use in acidic ground conditions combined with imperfections in the quality of galvanising can lead to failure of galvanised steel poles in a significantly shorter time period.
Concrete poles are heavy and more challenging to handle than traditional wooden poles. The companies we work with who have used concrete poles tell us that the significantly greater weight of these poles bring new requirments in terms of transportation and lifting equipment plus new challenges in conducting a safe and efficient installation process. As a result, not only is the pole cost higher but also the installation cost . In addition, these poles cannot be easily climbed whilst the conductivity of steel is a major issue for many power distribution companies.
The use of alternative pole materials can also have a significant environmental impact especially when it comes to CO2 emissions from pole manufacture. The majority of utilities have CO2 reduction targets as part of their commitment to corporate and social responsibility. The use of alternative pole materials can have a significant impact on meeting these targets. Whilst wooden poles typically capture and store around 320kg of CO2 from the atmosphere, the manufacture of poles from alternative materials generates significant amounts of CO2.
For instance for a typical utility that replaces 30 thousand poles a year, a switch from wooden poles to galvanised steel poles will see CO2 emmisions increase by 33,000 tonnes a year. Whilst switching to concrete leads to an increase in emmisions of 53,000 tonnes with the use of composites increasing emmisions by 35,000 tonnes a year*.
*Source “Conclusions and summary report of an environmental life cycle assesment of utility poles” Prepated by AquAeTer Inc.
In the first of this series of blogs (click here) we covered the causes of wooden pole failure and the methods of preventing this in detail. To summarise wooden utility poles typically fail as a result of decay at the critical ground line section of the pole as the effectiveness of wood preservative diminishes over time due to oxidation and leaching. This leaves the pole vulnerable to decay, loss of strength and failure. Decay starts at the mechanically highly stressed pole section in the upper 200mm (8″) of the ground where condions are ideal for decay with high moisture content oxygen and higher temperatures creating the perfect environment for decay to occur. Deeper in the ground and above ground the conditions for decay are not generally present and failure at these points is highly unlikely. The use of additional protection at the vulnerable ground line section of the pole provides a highly effective and proven means of overcoming the traditional weakness of wooden poles; ground line decay. In the next section we will look at the options for achieving this.
Barrier products provide additional protection to a wooden pole at the vulnerable ground line section of the pole and work in conjunction with the wood preservative to increase pole service life. Barrier systems come in two types; Partial and Full barriers. Partial barriers are available in many forms such as a simple ground line wrap, self-adhesive tape, heat shrink tube, wrap with a metal foil behind the outer wrap or a complete pull-on “bag” that covers the whole in-ground section of the pole. Partial barrier systems have one thing in common – they do not seal the surface of the pole behind the sleeve or bag. This means that preservative can be lost from the wood behind the barrier and water can access the entire pole surface behind the outer barrier. Capilliary action between the outer sleeve and the wood “transporting” moisture from the ground to the top of the sleeve. This creates a damp or wet band at the top of the bag or sleeve allowing decay to occur at the top of the barrier or behind the barrier itself. Without entirely excluding moisture, oxygen, organisms and nutrients, there is still potential for decay to occur.
Total barrier systems have a meltable sealant behind the outer barrier. The sleeve is heat applied causing the inner liner to melt and seal the pole surface to form an air and watertight seal. This excludes all of the factors necessary for decay to occur including oxygen and moisture. This seal ensures that the wood at the top of the sleeve remains below the 25% threshold at which decay can start whilst preventing any loss of wood preservative from the protected zone. Total barrier sleeves such as Polesaver make conventional ground line decay impossible.
Total barrier sleeve showing air and watertight seal to the pole surface behind the outer barrier
Graph showing projected loss of pole bending moment strength over time for standard preservative treated wooden pole and preservative treated pole protected with a Polesaver total barrier sleeve.
Alternative pole types of concrete, steel and composite may be advantageous in certain respects; however, wooden poles have shown to be more appealing from the viewpoint of cost, installation and environmental impact. Total barrier systems offer a proven and highly effective means of allowing wooden utility poles to match or better the life of alternative pole materials at significantly lower cost. In the next blog we will look in detail at partial and full barrier sleeves.
Richard is the founder and CEO of Polesaver. With over 26 years of experience in developing and testing Polesaver products, Richard is an expert when it comes to wood preservation.
Your email address will not be published. Required fields are marked *
Save my name, email, and website in this browser for the next time I comment.
Polesaver manufacturers and supplies guaranteed products that are proven to extend the life of utility poles. With over 7 million sleeves supplied to date, our patented ground-line barrier sleeves have been proven in volume use since 1994.
+44 (0) 1452 688094
Unit 7, The Hawthorns, Staunton, Gloucestershire, GL19 3NY, UK
Polesaver uses long term independent test data on the effectiveness of barrier sleeves and fire protection fabric to reach all the conclusions given on this website (test data available on request). Based on this data, Polesaver believes longer life, maintenance of strength over time, improved safety and reliability, extended inspection periods and reduced maintenance requirements are reasonable claims. This is subject to Polesaver products being correctly applied as per our instructions and used on correctly preservative treated (for long term in-ground use - use class 4 or higher) wooden utility poles that are free of decay at the time of sleeve application. The claims made, real or implied are not warranties. It is the responsibility of the user to evaluate and satisfy themselves that the performance of the product meets their specific safety, reliability, extended inspection, repair and any other performance or cost-benefit criteria before using Polesaver sleeves or fire protection fabric.